# Mathematical modeling of an air split-conditioner heat pump operation for investigation its exergetic efficiency

2020;
: pp. 169–178

Revised: May 03, 2020
Accepted: May 05, 2020
1
Department of Heat, Gas Supply and Ventilation, Institute of Construction and Engineering Systems, Lviv Polytechnic National University
2
Department of Heat, Gas Supply and Ventilation, Institute of Construction and Engineering Systems, Lviv Polytechnic National University
3
Department of Heat, Gas Supply and Ventilation, Institute of Construction and Engineering Systems, Lviv Polytechnic National University
4
Department of Heat, Gas Supply and Ventilation, Institute of Construction and Engineering Systems, Lviv Polytechnic National University

In the modern technologies related to energy transformation, namely in the field of heat pumps of air split-conditioners (“air-to-air”), an important place is occupied by apparatuses and processes, which energy perfection can be objectively evaluated only on the basis of analysis of their exergy efficiency. This allowed substantiating the actuality of the research task due to insufficient information on the exergy efficiency of the use of heat pumps of air split-conditioners and their elements. The author’s innovation mathematical model for the analysis of the operation of one-step freon heat pumps, which are used in air split-conditioners, according to the exergetic method, is developed. In this article analyzes the exergetic output-input ratio (OIR) and the losses of exergy in the separate elements of heat pumps of air split-conditioners on the example heat pumps of air split-conditioners with a nominal heating capacity of 2500, 2840, 3580, 5620, 6400W by “Daikin” firm in the standard external temperature conditions on the refrigerant R410A are obtained on this model. It has been determined that, by exergy efficiency, heat pumps of air split-conditioners with higher heat capacity have lower exergy efficiency. In our opinion, this is due to the incorrect acceptance of air flow rates on the evaporator and condenser, which do not correspond to the heat balances of these apparatuses and the same internal temperature regime for different heat capacity heat pumps of air split-conditioners. An example is the Grassman’s diagram of the heat pump of air split-conditioner with the heat capacity of 2500W. The losses of exergy having been established in all elements of heat pumps of air split-conditioners indicate that the air split-conditioner parts should be improved to reduce the losses of exergy in them and to increase its exergetic OIR in general.

1. Energy Strategy of Ukraine until 2030, http://www.ukrenergo.energy.gov.ua (in Ukrainian).
2. Heat Pump, Types and Applications of Heat Pumps, http://www.ecosvit.net/ua/teplovij-nasos-vidi-ta zastosuvannya (in Ukrainian).
3. Heat pumps, http://www.npblog.com.ua/index.php/hi-tech/teplovi-nasosi.html (in Ukrainian).
4. Bezrodnyi M. N., Dranik T. V.  Thermodynamic Efficiency of Heat Pump Application for Providing Comfortable Conditions in Indoor Swimming Pools.  Eastern European Journal of Enterprise Technologies. 3 (8), 25–30 (2013).
5. Matsevityi Yu. M., Chirkin N. B., Bogdanovich A. S., Klepanda A. S.  Introduction of Heat Pumping Technologies. Ecotechnology and Resource Saving. 3, 4–10 (2008), (in Russian).
6. Zalewski P. K. Pompy ciepła. Podstawy teoretyczne i przykіady zastosowania. Krak\'{o}w (1995), (in Polish).
7. Szargut J., Petela R. Exergy. Moscow, Energy (1968), (in Russian).
8. Sokolov E. Y., Brodyansky V. M.  Energy Basis of Transformation of Heat and Cooling Processes. Moscow, Energoizdat (1981), (in Russian).
9. Morozyuk T. V.  Theory of Refrigeration Machines and Heat Pumps. Odessa, Studio ``Negotsiant'' (2006), (in Russian).
10. Silvio de Oliveira Jr. Exergy. Production, Cost and Renewability. Springer (2013).
11. Sazhin B. S., Bulekov A. P., Sazhin B. S.  Exergy Analysis of Work of Industrial Plants. Moscow (2000), (in Russian).
12. Bejan A.  Advanced Engineering Thermodynamics. New York, John Wiley & Sons (1988).
13. Bejan A., Tsatsaronis G., Moran M.  Thermal Design and Optimization. New York, J. Wiley (1996).
14. Morosuk T., Nikulshin R., Morosuk L.  Entropy-Cycle Method for Analysis of Refrigeration Machine and Heat Pump Cycles.  Thermal Science. 10 (1), 111–124 (2006).
15. Tsatsaronis J.  The Interaction of Thermodynamics and Economy to Minimize Cost of Energy Conversion Systems. Odessa, Studio "Negotsiant" (2002), (in Russian).
16. Labay V., Dovbush O., Yaroslav V., Klymenko H.  Mathematical Modeling of a Split-conditioner Operation for Evaluation of Exergy Efficiency of the R600A Refrigerant Application.  Mathematical Modeling and Computing. 5 (2), 169–177 (2018).
17. Labay V. Yo., Khanyk Ya. M.  Energy Saving Ratio Between the Air Flows at the Evaporator and Condenser Air Split-conditioners.  Refrigeration Engineering and Technology. 6 (116), 28–31 (2008), (in Ukrainian).
18. Labay V. Yo., Mysak Yo. S.  Adduction of Work of Refrigeration's Machines of Air Split-conditioners to the Identical Internal Temperature Condition.  Refrigeration Engineering and Technology. 4 (126), 19–22 (2010), (in Ukrainian).
19. Jakobsen A., Rassmussen B.-D., Skovrup M.-J., Andersen S.-E.  CoolPack – a collection of simulation tools for refrigeration systemes. Tutorial. Version 1.46.   Department of Energy Engineering Technical University of Denmark (2001).
20. Daikin Catalog Split (2017).
Mathematical Modeling and Computing, Vol. 7, No. 1, pp. 169–178 (2020)