Replacement of old wooden windows in a new plastic windows, in the old buildings, we achieve the massive reducing heat loss of the building. New windows are characterized by better tightness. The question is, how much more are reduce the uncontrolled ventilation. In the article is presented the experimental measurement indoor air quality in the room in two phases. In the first phase is in the room installed 55 year old wood window. In the second phase is in the same room installed new plastic window. From the experimental measurement indoor air quality is calculated intensity of ventilation – infiltration. These resultant intensity of ventilation are reciprocally compared. The aim of the article is to find, on the basis of the experimental measurements, the difference in volume flow of air in the room by infiltration, which caused by the replacement of the old wooden window with a new plastic window with insulating double glazing. According to the analysis, it can be stated that by replacing the old wooden window in the room with a new plastic window, the volume of air flow caused by the infiltration decreased by approximately 73 %. The total window heat loss was reduced by
1. Wyon D. P. The effects of indoor air quality on performance and productivity. Indoor Air, Vol. 14, 2004, Issue 7. pp. 92–10, ISSN 1600-0668. 2. Koskela H., Maula H., Haapakangas A., Moberg V. and Hongisto V. Effect of low ventilation rate on office work performance and perception of air quality – a laboratory study. In: Proceedings of Indoor Air, 2014, Hong-Kong, Vol. 2, pp. 673–675. 3. Persily A. Evaluating building IAQ and ventilation with indoor carbon dioxide, ASHRAE Transactions, 1997, 103: 193–204. 4. Persily A. What we think we know about ventilation? in 10th International Conference on Indoor Air Quality and Climate “Indoor Air 2005”, 4–9 September 2005, Beijing, China, 2: 24–39.
5. Voznyak O., Myroniuk K., Sukholova I. Zastosuvannya povitrorozpodilu vzayevodiyeyu zustrichnyh nespivvisnyh strumyn – Zbirnyk MOTROL, Tom 13 C, – Lublin, 2011 (in Ukrainian) – С. 24 – 31. 6. Zhelykh V., Ulewicz M., Spodyniuk N., Shapoval S., Shepitchak V. Analysis of the Processes of Heat Exchange on Infrared Heater Surface. Diagnostyka. – Vol 17, No 3. 2016. – p. 81 – 85. 7. Bullová I. (2011). Problémy pri výmene okien v budovách na bývanie (Problems when replacing windows in residential buildings). In: Správca bytových domov. ISSN 1336-7919. Vol. 6, No 5, pp. 58-62. 8. Budaiova Z., Vilcekova S. (2015). Assessing the effect of indoor environmental quality on productivity at office work. SSP – journal of Civil engineering Vol. 10,. Issue 1. 2015. 9. Ulewicz M., Zhelyk V., Shapoval S., Spodyniuk N., Vengryn I.. Comparison of efficient of the combined solar collector for energy-efficient buildings for different modes of operation. Visnik Nacionalnovo universitetu “Lvivska politechnika”, Teoria i praktika budivnictva. ISSN 0321-0499, No 844, 2016, p. 352–355. 10. Bullová I. Wind action on the building faсade and Its influence on ventilation heat losses. Visnik Nacionalnovo universitetu “Lvivska politechnika”, SCTP. Volume 844, 2016.