The concentration of total iron is one of the main physicochemical indicators of the safety and quality of tap water. The standard amount of the concentration of common iron in tap water is not more than 0.2 mg/dm3. In some cases, due to specific natural conditions and technology for drinking water preparation/treatment, this number may be increased to 1.0 mg/dm3. Excess iron concentration in the water adversely affects the skin, blood composition, etc. Prolonged consumption of water with high iron concentration leads to liver disease, causes allergic reactions, etc. The analysis of groundwater quality in the territory of the Lviv region shows the increased total iron concentration in water of some water intakes. However, even relatively normal spring water quality and satisfactory operation of pipe water treatment plants, cannot prevent it from secondary pollution in the distribution networks of the water supply system. The Residents of Ukraine use household filters for additional purification of drinking water, including cartridge type. The purpose of the study was to compare the effectiveness of the iron removal from drinking water with household filters of the brands Nasha Voda (Ukraine), BRITA (Germany) and Aquafor (Russia). An experimental research of the filters was performed to determine the dependence of the iron concentration in the filtrate on the volume of the filtered model solution. During the preparation of the model solution, water was used from the water supply system of the city of Lviv, selected in the area of S. Bandera street with a starting iron concentration amount of 0.02–0.3 mg/dm3. After being passed through 15, 15 and 2.5 dm3 of the filtrate, for the filters Nasha Voda, BRITA and Aquafor respectively in the beginning of the experiment, the concentration of iron in the filtrate decreased and reached the normative value of 0.2 mg/dm3. The filtrate volumes passed through Our Water, Nasha Voda, BRITA and Aquafor filters were 210, 350 and 80 dm3 respectively. The slow filtration rate of the water through the Aquafor filter made it impossible to carry out the experiment after filtering 80 dm3 of the model solution. Tested filters have shown positive results in reducing the total iron concentration in water. However, it is recommended to apply the known methods of ironing on water treatment plants of settlements for iron removal from drinking water, particularly from tap water.
Borzunova, E. A., Kuzmin, S.V., Akramov, R.L., & Kiyamova, E.L. (2007). Assessment of the impact of water quality on public health. Hygiene and sanitation, 3, 32-34 (in Russian).
Ivanov, A. V., Tafeyeva, Ye. A., Davletova, N. Kh., & Vavashkin, K. V. (2012). Modern ideas about the impact of drinking water quality on public health. Chemistry and Ecology, 3, 48-53 (in Russian).
Mokiienko, A. V. (2015). Mineralnyi sklad pytnykh ta mineralnykh vod yak faktor vplyvu na zdorovia naselennia (ohliad literatury). Voda: gigiena i ekologiya, 3 (1-2), 50-60 (in Ukrainian).
Omarova, A. O., Tussupova, K. M., Berndtsson, R., & Kalishev, M.G. (2017). Medical and social significance of water supply, sanitation and hygiene in human activity. Vestnik KazNMY, (Vol. 3, pp. 193-197).
Shovkun, T., & Shovkun, I. (2018). Yakist pytnoi vody ta yii vplyv na stan zdorovia naselennia Chernihivskoi oblasti. Nauk. zap. Ternop. nats. ped. un-tu im. V. Hnatiuka. Ser. Heohrafiia, 1, 167-173 (in Ukrainian).
Stepanenkov, H. V. (2015). Vplyv yakosti pytnoi vody na stan zdorovia naselennia Poltavskoi oblasti v 2001-2012 rokakh. Visnyk Poltavskoi derzhavnoi ahrarnoi akademii, (1-2), 160-164 (in Ukrainian). https://doi.org/10.31210/visnyk2015.1-2.36.
Volkova, L. A., & Kushniruk, Yu. S. (2012). Yakist pytnoi vody yak pokaznyk medyko-ekolohichnoho ryzyku terytorii. Heohrafiia ta turyzm, 19, 316-323 (in Ukrainian).
Prokopov, V. O. (2012). Otsinka yakosti pytnoi vody z pidzemnykh vododzherel Ukrainy z pohliadu vplyvu na stan zdorovia naselennia. Naukovyi visnyk Natsionalnoho medychnoho universytetu imeni O. O. Bohomoltsia, 4, 122-126 (in Ukrainian).
Stavytskyi, E. A., Rudko, G. I., & Yakovlev, Ye. O. (Eds.). (2011). Strategy of drinking groundwater resources use for water supply (Vol. 2). Chernivtsi: Bukrek (in Ukrainian).
Matsiyevska, O. O. (2013). Yakist pytnoi vody, shcho nadkhodyt u merezhu tsentralizovanoho vodopostachannia m. Lviv. Kharchova nauka i tekhnolohiia, 1 (22), 87-89 (in Ukrainian).
Matsiyevska, O. O. (2015). Study of water quality in the distribution network of the centralized water supply system in the city of Lviv. Eastern-European Journal of Enterprise Technologies, 6(6), 62-70 (in Ukrainian). https://doi.org/10.15587/1729-4061.2015.56225.
Mika, A., Sekuła, K., Dendys, M., Ptaszek, W., & Postawa, A. (2018). Drinking of tap water is smart, but how do it better? - A tap water quality research. E3S Web Conf., Wastewater and Energy in Smart Cities, 30, 01007. https://doi.org/10.1051/e3sconf/20183001007.
Ponomarenko, N. P., & Korshun, M. M. (2014). Otsinka yakosti hospodarsko-pytnoho vodopostachannia raioniv Chernihivskoi oblasti. Aktualni problemy suchasnoi medytsyny. 14(2), 37-43 (in Ukrainian).
Safranov, T., Polishchuk, A., Yurchenko, V., & Yaryshkina, L. (2016). Otsinka optymalnosti mineralnoho skladu pytnykh vod system tsentralizovanoho vodopostachannia okremykh miskykh ahlomeratsii Ukrainy. Visnyk Kharkivskoho natsionalnoho universytetu imeni V. N. Karazina seriia "Ekolohiia", (15), 89-98 (in Ukrainian).
Zorina, O. V. (2018). Hihiienichna otsinka yakosti vodoprovidnykh pytnykh vod za sanitarno-khimichnymy pokaznykamy u malovodnykh rehionakh Ukrainy. ScienceRise. Biological science, 3, 33-39 (in Ukrainian). doi:10.15587/2519-8025.2018.135625.
Matsiyevska, O. O., Dolinska, N. V., & Shevchuk I. Z. (2009). Eksperymentalne porivniannia roboty filtriv dlia pomiakshennia vody kartrydzhnoho typu. Visnyk Natsionalnoho universytetu "Lvivska politekhnika": Teoriia i praktyka budivnytstva, 655, 178-182 (in Ukrainian). http://ena.lp.edu.ua:8080/handle/ntb/2923.