The issue of the normative air exchange ensuring in the premises of the boiler houses is extremely important. The article presents the results of theoretical and experimental studies of air velocity determination in the distribution of air by round and compact jets in the boiler room. Graphical and analytical dependences are given. The research results substantiate the higher accuracy of the average air flow velocity determination in small boiler rooms.
In this article the results of return flow at air distribution by flat laying jets experimental investigations are presented. The chart is composed, analytic equations are also obtained. By these results high efficiency of proposed air distribution scheme using in technological small-sized rooms is shown.
The article presents a model of a signal generated by microparticles moving in an aerodynamic flow. This model is based on the Lorentz–Mie scattering theory. It is shown that the visibility and the signal/noise ratio of the Doppler signal are determined by the degree of amplitude and polarization matching of the scattered waves. These parameters also depend on the degree of phase matching of "elementary" Doppler signals. Using this signal model, it is possible to calculate the shape of the aperture of the receiving optics for a specific type of laser Doppler anemometer. The use of such
The sucker-rod oil pumping unit productivity is influenced by lots of factors, including the operation mode of the jack pump electric drive system. Settings of the electric drive system affect the system’s energy indicators, overhaul period and oil production volume. Therefore, an effective operation of oil production units is an important factor influencing the cost of the produced oil. The paper proposes a method of selecting the speed of the driving motor of the jack pump electric drive that allows balancing the sucker-rod oil pumping unit productivity and the reservoir flow rate.
Air distribution by spread air jets has been regarded. Coefficient of convective heat and heat amount have been determined at air jets spreading on enclosure surface.
Air distribution by interaction of counter non coaxial air jets at pulsing mode has been considered. Dynamic parameters of air flow that is created due to interaction of counter non coaxial flat air jets at their leakage at pulsing mode and creation of dynamic indoor climate in a room has been determined.
Air distribution in a room by swirl and spread air jets has been regarded. Dynamic parameters of air flow that is created due to swirl and spread air jets at their leakage in a room has been determined. Jet spun at an angle of inclination jet twisting plates 90˚ similar in its characteristics to upstream. Grazing jet develops independently of swirling, ie no jets interaction. At an angle of 60˚ tilt plate twisting jet flooring jet also develops independently of swirling, ie no jets interaction.